Do you have a question about your Salus iT500 Smart Thermostat? Explore Salus videos, user guides and FAQ’s for more information.
iT500 Internet Thermostat Installation
iT500 One Zone
SALUS iT500 Thermostat – Product Help Video
iT500 from SALUS Controls
iT500 Two Zones
iT500 App Promo UK
Yes, most functions can be operated from the iT500 unit.
heck that the screen lock is not active. If active, there will be a padlock visible in the top of the LCD. Disable by pressing and holding top two left keys on the iT500.
Check that the iT500 is in AUTO mode, ‘AUTO’ should be visible at the bottom right on display. If showing ‘OFF’ press the TICK and SETTINGS buttons, then use the UP/DOWN arrow keys to change OFF to AUTO then TICK to confirm.
Check the gateway is plugged into the router and it has a green light.
Position the iT500 within 1 meter of the SALUS Gateway unit.
If you receive the message ‘Failed’ please try running the OTA again. (Due to internet speed this may take several attempts)
If you have an iPhone, please search for iT500 on the app store, if you have an Android; search for iT500 on Google play.
It lets you control the iT500 remotely over the internet. You have full remote access to your heating control giving both temporary and program changes.
Check you received your confirmation email from SALUS and clicked on it.
Check you entered the correct email and password as used on registration.
Ensure you added your device STA number which is located in the battery compartment of the iT500.
You should see an image of your device after log-in, click on it to access.
Check that the top slide switch on the receiver unit is in the AUTO position.
Perform a quick installation check by putting the top slide switch to Manual position, and the bottom slide switch to CH. The boiler should fire, if not the iT500 receiver may be wired incorrectly. Please contact your installer.
A flashing Blue light is normal indication that the iT500 thermostat is asking for heat and the boiler should be on.
A flashing Yellow light is fault indication. The iT500 receiver unit has lost communication with the thermostat. Check the thermostat distance from its receiver, and check for major metalwork in its communication path (such as fridge/freezers). Reposition the thermostat to improve communication. Once it establishes communication again the fault will clear automatically.
Check that you have the power supply turned ON to the gateway and it has a steady green light showing.
The green light indicates you are connected to the SALUS server.
If you have all the above, remove a battery from the iT500 and replace after 10 seconds. This will reboot the iT500 and bring you back online.
The gateway must be connected to a network that has DHCP enabled, it must be connected to a network that has the firewall ports 80 (UDP/TCP) and 2165 (TCP) open. (You may need to contact your internet provider to assist you changing your router settings.)
BT Hub 5 uses ports 3 and 4.
Have you paired the thermostat with the receiver, please see page 15 in the installer manual on how to do this.